Please Read All Instructions Attempting Installation
-To prevent personal injury or product damage only licensed electricians should install.
-To avoid electric shock or component damage disconnect power before attempting installation or servicing.
-This product must be installed in accordance with the national electric code(NEC) and applicable federal, state and local electric codes and safety standards.
-Disconnect product and allow cooling prior to servicing.
-Any alteration or modification of this product is expressly forbidden as it may cause serious personal injury, death, property damage and/or product malfunction.
-To prevent product malfunction and/or electric shock this product must be properly grounded.
-This luminaire is designed to operate in ambient temperatures ranging from -30℃ to 45℃ and to be horizontally mounted with the LEDs facing down.
-Wall mount only.
Thoroughly inspect the fixture for freight damage. Freight damage should be reported to the delivery carrier.
1).Take off the screw of the heat sink and take off the front lid carefully from the back. The angle between the front cap and the back cap should be 0-45 degrees.
2).A: After determining a place to put a conductor, take off the 1/2” cap and make a hole according to the example(B). Fix it on the wall with an appropriate screw.(Please use glue to block the hole to prevent water leakage.)
B: When installing the junction box, take off the 1/2” cap of the C wire in the middle. This product supports standard 3 1/4” and 4” junction box. After installing the back cap on the wall, use waterproof sealer to seal it.
3).Link A wire and C wire (The black one is L, white one is N, and the yellow one is groud wire), installing the front cap.
4). Make sure the wires are all linked rightly, and lock up with the screw.
Installation of the photocell
Photocell input voltage range 120V or 277V, 60HZ,
1).Pick a 1/2” cap of either side of the product and install the photocell according to the picture.
2).Complete the photocell system after installing the photocell.
- Are the wired linked in a right way as the picture shows?
- Is the ground lead installed appropriately?
- Make sure the photocell function well.